A world leading engineering company recently contacted Impact to organise a site visit, the purpose of the site visit was to assess ventilation requirements to control the solvent vapours produced during the application of bonding substances to metal parts within an existing enclosure.
Impact Technical Services installed a new ducted system to the top of the enclosure using galvanised spiral wound ducting.
A new 1.1kW fan with spark minimising features was installed upon the false ceiling above the bonding area complete with new external discharge stack & high velocity cowl to disperse the extracted solvent vapours safely to atmosphere above the roof line of the building.
The new system was installed & commissioned to meet requirements of HSG 258 Controlling Airborne Contaminants at Work.
If you require any help regarding dust and fume extraction then contact the experts at Impact:
Call – 0116 2448855
Email – [email protected]